Question about Friedrich QuietMaster Deluxe RS12L10 Air Conditioner
My 4 year old son put the unit on heat and then had it still on the blue cold. Now the unit wont come on. We try the the reset button but it never trip or does anything
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hi, Reduced air flow, low on freon or being continuously run during cooler weather such as at night. Some people turn their thermostat on 60 thinking that it will help get it cooler faster. They freeze up at night and don't get a chance to thaw during the day. It needs set no lower than 75 or so. The evaporator may be dirty. Don't know a lot about your particular unit but if the outside unit has the compressor and refrigerant lines running to it, The large refrigerant line should sweat all the way to the compressor if its fully charged. Please rate me if I have helped. Good luck kstfas
Posted on Aug 28, 2007
Low voltage shorts can be a real pain to find!!! i would try a process of ellimination: first i would try to elliminate the thermostat. then id look for a wire that is vibrating on something in the cabinet.
Posted on Oct 16, 2007
SOURCE: Friedrich wiring diagram
COPY PASTE THIS TO YOUR WEB BROWSER TO LOCATE YOUR MANUAL AND DIAGRAM...:)
JUST GO TO THE WEBSITE FOR CLEAR DIAGRAM.
Posted on Jan 20, 2008
A squealing noise is most likely the bearings going bad in the blower motor. This will slow the motor down. If the blower is not operating at the proper speed this will affect the temperature pressure relationship of the refrigerant. This will cause the unit to put out the wrong temperature. Running the unit to long under these conditions can possibly cause further problems ( including a very high electric bill). I recommend that use do not use this unit untill it is repaired or replaced.
Posted on May 03, 2009
likely is the thermostat or could be the compressor going out on over load compressor runs blows cold air trips out on the over load fan will stay running jumper out the thermostat see if it stays running.like1/2 hr. if it does replace the thermostat not hard to change if you can find one.Tom
Posted on Jun 18, 2009
Tips for a great answer:
Oct 01, 2015 | Friedrich Heating & Cooling
Dec 08, 2013 | Friedrich CP06C10 Wall/Window Air...
Dec 07, 2013 | Friedrich VEA09K34 Packaged Units,electric...
Oct 29, 2013 | Friedrich YM18L34 Thru-Wall/Window Air...
Aug 03, 2011 | Friedrich QuietMaster KS15L10...
Jul 23, 2011 | Friedrich CP10E10 Thru-Wall/Window Air...
Jun 09, 2011 | Friedrich CP06C10 Wall/Window Air...
Dec 14, 2010 | Friedrich EL36L35 TwinTemp® 36000 BTU...
Apr 29, 2010 | Heating & Cooling
74 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: