Question about Heating & Cooling
SOURCE: Vaillant Ecotec combi boiler -
The fact that you're getting a little burst of domestic hot water suggests that the boiler is capable of circulating hot primary loop water through the heat exchanger, but doesn't necessarily do so when it needs to.
What seems to be lacking is a recognition that domestic hot water is now being drawn off, and that the boiler needs to fire up and divert the primary flow through the heat exchanger.
A good place to start might be the flow switch (usually in the bottom of the boiler, where the cold water supply comes in) or the electrical connections to it.
Posted on Oct 07, 2008
SOURCE: Vaillant combi boiler problem
when the tap is turned on and the water light on the boiler doesn't this means the diverter valve is not operating it could be down to low water pressure in the house this can be checked at the cold tap in the kitchen. if there is plenty of pressure then it could be the diagphram in the diverter valve is worn or split. the diagphram is only a few pounds but it depends on the engineer you get as to how much money he wants to fit it.
the egg timer symbol (or two pyramids together) is an ignition indicator turn off and on again to see if it will fire with the tap running. reset the boiler with the lower right hand control knob.
Posted on Mar 26, 2009
Tips for a great answer:
Nov 17, 2015 | Water Heaters
Nov 20, 2013 | Computers & Internet
Jan 11, 2013 | Computers & Internet
Oct 27, 2012 | Water Heaters
Oct 27, 2009 | KDS Valiant 6380iPTD-01 Notebook
Oct 05, 2008 | Heating & Cooling
Apr 26, 2017 | Heating & Cooling
65 people viewed this question
Usually answered in minutes!