Were is the reset button on the unit?
Hi, here is the theory on the reset button on Air Conditioners. They reset via the breaker panel box in your house. Check that first before anything else. However if your unit is popping breakers, it is because the rating for the breaker is incorrect, or there is something that needs servicing usually in the outside unit called the condenser. That piece contains the compressor. A faulty compressor and pop the breaker. Or If the condenser fan that blows over the coils of the outside unit stops (common failure) The compressor will overheat and shut down. That may not trip the breaker but the house will get hot anyway. Usual action for this is to replace the condenser fan motor and starting capacitor. Make sure the speed rating and directional rotation for the replacement motor is the same as the motor removed.
There are other reasons why the system won't come one fully. If the wall thermostat is digital and does nothing. including turning on the fan. There will be a small fuse located on the circuit board of the air handler (part of Air Conditioner mounted inside the house. It houses the circulation fan). That fuse could be blown. That one shuts down just about everything.
On air handlers mounted up into the attic crawl space there is an overflow pan. This pan is mounted directly below the air handler. This pan can fill with water when the drain pain contained inside the air handler starts to overflow because the drain system to that is clogged.
There is a "float switch" mounted in the overflow pan wired to the system in such as way as to shut down the entire AC system if that pan fills.
The handling is to clear the obstruction in the Drip Pan inside the air handler. Then remove enough water from the overflow pan and the AC will run as though nothing has happened.
If you have more questions, write to me on this site.
One thing more. The capacitor alone in the Outside condenser unit can fail and that will stop the condenser completely if it is of a "split" design and used for both the compressor and fan. When replacing this unit alone, ALWAYS find the same specification part.
I hope this helps,
Have a Happy New Year,
Jan 02, 2011 |
Goodman CLJ30AR32 Air Conditioner