Question about Ruud Heating & Cooling
Check and find out if you have 24 volts across the terminals for the coil of the contactor. If you have 24 volts across the terminals and the contactor does not pull in change the contactor with one of the same ratting. If you do not have 24 volts across the terminals for the contactor coil your problem in in the 24 volt circuit. Possible that the thermostat is not sending power to the contactor through the "Y" terminal.
Posted on Jul 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 03, 2015 | Heating & Cooling
Mar 30, 2014 | Rheem 4 Ton Air Handler - RHLLHM4821JA
Feb 13, 2014 | Intertherm Heating & Cooling
Jan 02, 2011 | Goodman CLJ30AR32 Air Conditioner
Aug 26, 2010 | Goodman CLQ36AR49 Air Conditioner
Jun 17, 2010 | Heating & Cooling
Jan 15, 2010 | Omega Trane Furnace Draft Inducer Blower...
Sep 27, 2009 | Ruud Central System Air Conditioner
Aug 17, 2009 | Heating & Cooling
87 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: