Question about Mitsubishi Mr. Slim MXZ30TN Air Conditioner
Electric service to outside unit is proper.on start up unit works perfect,after a few hours it starts to draw 40 amps from its normal 10 amps.it will go up and down every 2 seconds then throw the 20 amp breaker?
Sounds to me like yo have dirty condenser coils (outside unit) After this runs and gets hot it loads the compressor because it can not release heat out of the condenser coil it also may have a restriction somewhere on the high side that could cause this maybe in a txv or in a line filter.
Hope this helps Ya
please rate me
Posted on Jul 20, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 25, 2015 | Heating & Cooling
Jun 30, 2014 | Friedrich X-Star XQ10L10 20" Air...
May 27, 2014 | MR SLIM Split-ductless: Mitsubishi...
Oct 15, 2013 | Mitsubishi MSZ-FE12NA MUZFE12NA Mr Slim...
Mar 22, 2011 | Mitsubishi Heating & Cooling
Jul 10, 2009 | Heating & Cooling
Dec 11, 2008 | Heating & Cooling
Aug 29, 2008 | Amana PTH123B35AJ Air Conditioner
216 people viewed this question
Usually answered in minutes!