Question about Goodman CLQ36AR49 Air Conditioner
We have a Goodman GSC13 - 13 SEER. Fan in attic, compressor outside.
Fan in attic, compressor outside.
It worked fine for the first 2 weeks. Then one afternoon we realized it was pumping out hot air and that the compressor wasn't running. We turned it off, tried an hour later, same problem.
AC guys came next day--turned it on--it worked fine. They checked everything, couldn't find a problem.
This afternoon it started blowing hot air again, compressor not running.
The temp outside was 91, heat index 97.
The 1st time this happened it was a very hot day too.
Problem seems to be that when the outside temp or heat index hits mid 90s or better the compressor stops. Any ideas? Thanks for any help.
I believe you have 1 of 2 problems going on here your system may be overcharged causing the compressor to cut out on a overload relay circuit internally, or it also could be tripping out a high pressure switch which could be from an overcharged system or a dirty condenser. I would have the tech come out on a 90 degree day and put the gauges on and check the pressures while it is operating under a full load.
Hope this helps you.
Please rate me
Posted on Jul 19, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 15, 2013 | Goodman Manufacturing Goodman GSC130181...
Sep 27, 2012 | Goodman Manufacturing Goodman GSC130301...
Jun 28, 2012 | Heating & Cooling
Jun 06, 2011 | Goodman Heating & Cooling
Jun 07, 2010 | Goodman CLQ36AR49 Air Conditioner
Aug 12, 2009 | Heating & Cooling
Aug 12, 2009 | Goodman CKL60AR60 Air Conditioner
Jun 29, 2009 | Goodman CKL49AR49 Air Conditioner
Jun 13, 2009 | Ruud UAKA042 Air Conditioner
439 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: