Question about Carrier 38CKC036 Air Conditioner
The two terminal cap is only for the new fan motor. Connect the compressor wire back where you found it, on the 3 terminal cap. It's the terminal marked, "herm". The "common" terminal on the 3 terminal cap must still be connected to one side of the 220 power at the contactor. One side of the 220 goes to the common on the compressor. The other side of the 220 goes to the run winding on the compressor AND the common terminal on the 3 terminal capacitor.
Posted on Jul 22, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 11, 2013 | Heating & Cooling
Jul 22, 2008 | GE Heating & Cooling
Jun 28, 2012 | Heating & Cooling
Jul 09, 2010 | Heating & Cooling
Apr 05, 2010 | Heating & Cooling
Oct 11, 2009 | Dometic Rooftop RV Air Conditioner
May 31, 2009 | GE Heating & Cooling
May 06, 2009 | Heating & Cooling
Apr 27, 2009 | Heating & Cooling
Aug 25, 2008 | Goodman CKL60AR60 Air Conditioner
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
336 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: