Question about Ruud UAKA037 Air Conditioner
I just replaced fan mortor and capacitor. Fan first came on strong, then slowed down. I told my wife maybe the newer motors work like this. Well the compressor wouldn't come on. Now compressor comes on, and fan doesnt' . This is a brand new fan? Is there something else I need to look at? I've checked connections as best I can, all breakers, and disconnect, and all seem to be right.
Not all new fan motors are good, hows your luck been running?dose it turn freely? i would take it back for replacment dan
Posted on Jul 19, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2015 | Snap-On Welding Tools
Sep 18, 2008 | Dometic Rooftop RV Air Conditioner
Mar 02, 2017 | Heating & Cooling
I just had the same problem. I replaced the motor with no luck. It turned out to be a bad capacitor. If it is a dual capacitor, three prongs on top, it also starts the compressor. It is recommended to replace the capacitor anytime you replace a motor. I would try replacing the capacitor first. It is a lot cheaper that a new motor. If that does not fix the problem then you can get a motor. No harm, no foul. The slow start of the motor is a common symptom of a bad capacitor. The motor is not getting enough voltage. The capacitor increases the voltage like a transformer. It will boost it to almost 400 volts, depending on your unit.
Jun 21, 2012 | Heating & Cooling
May 09, 2011 | Weather King 10AJA3601AH Air Conditioner
May 31, 2010 | Heating & Cooling
May 29, 2010 | Cfm 802 Ecofan Table
Aug 02, 2009 | Heating & Cooling
Apr 23, 2009 | Heating & Cooling
122 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: