Question about Goodman Heating & Cooling
First stop pushing the contactor in if it tripped the breaker than you have a short and it need to be checked out the small wires are the t-stat wires could have shorted the control tranformer have the system looked at by your hvac people dan
Posted on Jul 19, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 10, 2017 | Goodman Heating & Cooling
Jun 18, 2014 | Goodman Heating & Cooling
Jun 10, 2012 | Goodman Heating & Cooling
Jun 13, 2010 | Goodman CKL60AR60 Air Conditioner
Jun 04, 2010 | Goodman CLQ36AR49 Air Conditioner
Aug 16, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 07, 2009 | Goodman CKL24AR24 Air Conditioner
Jun 25, 2008 | Goodman CLQ36AR49 Air Conditioner
50 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: