Question about Minka Aire F812-IO Lineage? Fan
We had the lineage installed to a new home by an electrician and he could not get the upper lights to work but everthing else worked, the wall switch will not work at all and this is what operates the fan. can you please let me know what you think the problem may be?
If the wall switch will not work at all, but the fan still works this tells me the power is not being sent to the switch and back to the fan. If it is a single switch and the power starts at the fan there should be a black and white wire on the switch. (pull switch out of the wall to check...turn power off first!!) If so they did a switch loop and the power wire should be connected to the white wire up in the fan box and the power (black) wire connected to your fan lights and fan motor. You will also see your power feed cable consisting of a black and white wire. Black is your power and white is your neutral. That white wire will be connected to the neutral wires of your fan lights and motor. (Note: your fan will have to disassembled and taken down to diagnose this). Good Luck!!
Posted on Apr 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 24, 2013 | Hunter Dryers
Jan 11, 2011 | Intermatic Inc. ST01C Digital In-Wall...
Mar 01, 2010 | Leviton 5603-wh 3 Way Decora Switch
May 17, 2009 | Speed Ceiling Fan 3-speed Switch By...
Jan 15, 2009 | Leviton #601-6696-I Ivory Wireless 3WY...
Oct 20, 2007 | Hampton Bay 24002 Ceiling Fan
239 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: