Question about Heating & Cooling
take both frt skid plates off lift motor to ease pressure on mount undo mount center bolt raise motor abit more undo bolts to mount at motor
Posted on Feb 26, 2009
Check the frame mounts too. You will have to loosen the bolts and jack the motor up with a jack and a woodblock.
Posted on May 04, 2009
The pump is probably gone. the way it works is a float allows the water level to stay the same in the reservoir so check that. Water is pumped up to the hoghair and trickles down into it. A big old blower pulls the wet outside air into the room. We call that one a swamp cooler down here on the gulf. Go outside and spray some water on the unit to cool down the house till you can get the pump replaced.
Posted on May 10, 2009
Tips for a great answer:
Dec 10, 2012 | GE Profile Arctica 25.4 Cubic Feet...
Sep 25, 2012 | 2000 Jaguar S-Type
Jan 24, 2012 | Weather King 10AJA3601AH Air Conditioner
Jul 22, 2011 | AdobeAir Adobe Air 550 CFM Portable...
Jan 02, 2011 | Essick Air Credenza 696 400 5.2 Gallon...
Jan 01, 2011 | Mastercool 67680 Evaporative Cooler Air...
Aug 14, 2010 | Mastercool 67680 Evaporative Cooler Air...
Dec 17, 2009 | GE GSF25XGR Side by Side Refrigerator
May 06, 2009 | Mastercool 67680 Evaporative Cooler Air...
May 24, 2017 | Honeywell Heating & Cooling
May 24, 2017 | Heating & Cooling
84 people viewed this question
Usually answered in minutes!