Question about Delfield (F18WC60) Commercial Refrigerator
Just changed a bad compressor in this unit it was originally an R-12 unit i replaced it with R-409A and the unit will not get down to temp and the compressor is kicking out on high heat i did clean the condenser coils any ideas?
Very most likely overcharged on freon. With R-409-A, you can not charge by sight glass. Do the ambient plus 30 method if it is a txv. That will get you close. If it is a cap tube, charge to an evap temp of about 20 degrees. then watch it. Make sure it makes temp and shuts off.
Hope this helps
Posted on May 02, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 12, 2011 | Delfield Refrigerators
Jan 31, 2011 | Delfield 406 / 406-CA Refrigerator
Oct 11, 2010 | Delfield 406 / 406-CA Refrigerator
Aug 13, 2010 | Delfield 032-F2FH ColdPro Solid Door Reach...
Aug 11, 2010 | True GDM-41 Refrigerator
Apr 24, 2009 | Maytag MFI2568AE Side by Side French Door...
Feb 14, 2009 | Delfield 'New 6000XL 6051 Side by Side...
Dec 19, 2008 | Delfield 'New 6000XL 6051 Side by Side...
Dec 09, 2008 | Delfield 60 Refrigerated Work Top Model...
Aug 07, 2007 | Delfield 032-F2FH ColdPro Solid Door Reach...
929 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: