Question about Heating & Cooling
You could try resetting this as it could be caused by several factors (blown heat exchanger being one as Karl mentioned).
Hve you tried resetting from in Service Mode ?
To get to Servce mode you need to go ino User Setup Mode first (turn off the boiler via the panel switch - then hold the Lock/Reset button whilst turning back on). Once in User Setup Mode if you rotate the thermostats all the way clockwise (it should display the software version) Then press and hold the Lock/Reset button for 3 seconds.
This should put you into service mode and it is now possible to change/reset some of the control parameters.
If you try resetting the error.
This issue may be caused if the Flue or water stat is tripped (in which case reset the stat). If th Fan resistor remains open in the circuit then you will need tsomeone out to investigate as that may cause the GAS error too.
COuldalso be the Valve coils are faulty in wich case they need replacing (agians I would get an engineer outto confirm and do that).
I'm suyou probably tried all this but just in case...
If the roblem is solved can you advise what fixed it ?
Posted on Jul 01, 2013
Old one this question, but i have the same problem.
have checked stats ok.
it fires, but dies again.
it did run ok yesterday
What solved the starters problem?
Posted on May 04, 2017
My genie 35 is not lighting up what could this be can any body help
Posted on Jun 13, 2010
Sounds like you have 2 seperate problems here. The fault code GAS means that the boiler has failed to ignite. There could be various reasons for this so you really need to have it tested. Sometimes a leaking heat exchanger will cause this fault code to come up as well. A quick test to see if the heat exchanger is leaking internally is to remove the condense pipe under the heat exchanger when the pool pump is running but the boiler off. If there is water running out of it, then it is probably leaking.
The fault code gas does not have anything to do with a gas leak or a smell of gas. If there is a smell of gas, then do not use the heater untill it is checked by a Corgi registered engineer. If your boiler has a serial number which starts with 06 or 07 then you should contact Certikin as there is a recall on the gas isolation **** which could be the reason for the smell of gas. Alternatively you can contact ourselves at Kaltech as we are carrying out the recall.
Posted on Sep 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 08, 2016 | Cars & Trucks
on Nov 08, 2016 | Pool & Spa
on Aug 03, 2013 | Pool & Spa
Jul 28, 2015 | Pool & Spa
May 19, 2015 | Pool & Spa
May 28, 2010 | Rheem 266K to 399K BTU Swimming Pool...
Jul 11, 2009 | Raypak Versa 130,000 Btu Above Ground...
1,111 people viewed this question
Usually answered in minutes!