Question about Amana PTH123B25AJ Heat Pump Air Conditioner
Posted by Anonymous on
I don't think the Amana ASZ14 Heat Pump has a reset switch, but you can still reset it by resetting the power (when it's not running... turn your thermostat OFF first).
To reset the power, locate your circuit breaker box. There should be a double-breaker for the Heat Pump and another double-breaker for the Air Handler. Turn them both off for at least 2-3 minutes. Then flip them back on and turn your thermostat back ON.
You're thermostat may also have a RESET button that you can push. I have to reset mine every time I change the batteries in it.
Here are some more repair tips...
Heat Pump Troubleshooting & Repair:
Heat Pump Troubleshooting Repair
Amana ASZ14 web page:
ASZ14 Heat Pumps
Amana ASZ 14 SEER Technical Manual (45-page PDF):
Amana ASZ 14 SEER Technical Manual
Amana ASZ (and ASX) Service Instructions (66-page PDF):
Posted on Dec 16, 2015
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
as a general rule the lemon law does not effect acs. because the equipment colud be at fault, or the installer couild be at fault , or the installation or application coiuld be at fault, or the power company could be at fault or the ductwork inadquete or undersized? so there are so many variables that a new ac may not fix your problem so they rarely ever provide new.now lets discuss your insatller or dealer. why are they saying the rev valve is bad? let me say covs Changeover valves usually do one of three things. they stick in cool and wont shift so youare stuck in cool or sruck in heat. when energized you hear no kawhoosh sound and compressor doesnt change pitch. then they are stuck in heat or cool. what they do sometimes is stick halfway and that gives a coolish suction and a coolish line to the house but not real cold. the hot gas line is only warm and the discharge line is onlty warm. this means its stuck halfway. some times you can disconnect the fan run the pressures way up and gently tap the valve and it will free up. but it nay stick agagin. the valves in the compressor may also be weak and be misdiagnosed as as half stuck covalve.. you could close off the liquid line and see if the compressor cah pump down to zero . if it can't then compressor maY BE BAD .when the unit was installed did they put in a liquidline drier to collect impurities and protect the valve? its pretty unusual to see a valve fail and if to much heat is applied on replacement then new valve can be damaged. good luck , oh you have the option of requesting a different dealer if it is brand name like trane or american std with a parts and labor warranty. most dealers can honor the other guys warranty and get paid by the factory if you have lost confidence in your guy. i am sure you know right away if you got a budget jack leg job or a pro . good luck.
Posted on Oct 24, 2008
Tips for a great answer:
Jul 18, 2014 | Amana PTH093B35AJ 9100 BTU ThruWallWindow...
Oct 08, 2012 | Amana PTH093B35AM Thru-Wall/Window Air...
Jun 11, 2011 | Amana Heating & Cooling
May 14, 2011 | Amana PTH123B25AJ Heat Pump Air...
Nov 12, 2010 | Amana PTH153B50AE Air Conditioner
Oct 30, 2009 | Amana PTC153B35AJ Air Conditioner
Mar 16, 2009 | Amana PTC153B50AM Split System Air...
Jan 23, 2009 | GE Zoneline AZ38H12DAD Split System Air...
Jan 21, 2009 | Amana ARB2557CSR / ARB2557CSL Bottom...
Feb 02, 2016 | Amana PTH123B25AJ Heat Pump Air...
799 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: