Just paid over 1,500 last year an has not rungood since. starts up real good, but once aair is turned on it stops running, or it might run one air at times. on my way back to michigan an not a happy...
This generator is a 5KW model. This means it can supply up to 5000 watts of power, total. Not all devices list the watts they need to be provided - instead these devices list the power they need as volts and amps. This can make it hard to determine what the actual watt requirements are for the device.
Overly simplified, watts is equal volts times amps (watts = volts x amps). A single 120 volt light bulb that uses .833 amps consumes 100 watts. If you checked a regular 100 watt light bulb with an ammeter, you'd find it does indeed draw .833 amps.
Working the formula a different way, we can learn how many amps this 5000 watt generator can supply at 120 volts, too. If all the loads you need to connect to this generator are 120 volt types, that means the total amount of amps the generator can supply is 5000 watts / 120 volts = 41 amps purely resistive loads (like a toaster or light bulb) maximum under ideal conditions. There is never a time when ideal actually happens, and not all loads are purely resistive - many are inductive. Inductive loads are motors (like your A/C), fluorescent lamps, computer power supplies, etc. - so figure more like around 30 amps total instead.
If you try to connect devices that require more than 30 - 35 amps, the generator will probably have problems trying to supply this load for any longer that a short length of time. Additionally, motors like those in A/C compressors draw significantly more power when first starting and can cause the problem you are describing. Try running the generator with loads other then the A/C to see how well it can supply the load(s). Or try running only 1 A/C unit and other non-A/C loads.
What I'm trying to tell you is that you may need to do some active load management to be sure that you aren't trying to get more power out of the generator than it is capable of supplying. You may need additional generators or swap this one to a larger size to handle the load properly and safely.
I hope this helps & good luck!
Apr 09, 2011 |
Watts Onan Portable Generator - 5000 ,...