Question about Goodman CLJ30AR32 Air Conditioner
Copper pipes are iceing over. I shut it off and they melted. so I turned it back on and it was working but now the pipes are iced over again.
On a "Non Heat Pump" unit, icing of the pipes is not good. It is an indication that you either have a low freon level (Charge), low load, wrong superheat.
A low load usually means, in this case, something wrong with the air flow. Clogged filter, wrong fan speed, something blocking the return air grill, like a chair/ blanket, etc.
If low on charge, the evap (Indoor Coil) will ice up and the ice will then slowly creep along the pipe untill it gets to the outdoor unit. This is really no good. Air cannot go thru solid ice so naturally there is no cooling happening.
If a company replaces the outdoor unit (Condensing Unit), there is no warranty on the indoor unit. I do not know of any company that will repair an indoor coil (Evap). Just not smart money. They have to capture the freon, open the system, make the repair, ensure the correct level of freon is in the system, and most time, add a filter/ dryer for additional filtering and drying of the freon. With all that, no one is going to patch a leak on an old coil because if it leaks now, it's going to have another soon. You'll just be chasing leaks and spend money after money. Hope that makes sense. HVAC companys have to follow the EPA rules too. Leaving a system leaking above a certain percent of it's total charge is a major no-no. They will not do it.
Hope this helps clear up a few things and good luck.
Posted on Mar 20, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 15, 2011 | Coleman Heating & Cooling
Jan 26, 2010 | Heating & Cooling
Aug 19, 2009 | Dometic Rooftop RV Air Conditioner
Aug 13, 2009 | Hoshizaki Freezer Commercial Ice Machines...
Aug 13, 2009 | Heating & Cooling
May 20, 2009 | Weather King 10AJA6001AH Air Conditioner
Jul 22, 2008 | Heating & Cooling
Nov 13, 2007 | Whirlpool ED5VHGXM Side by Side...
Jul 05, 2013 | Goodman CLJ30AR32 Air Conditioner
Jun 20, 2011 | Goodman CLJ30AR32 Air Conditioner
152 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: