Question about Heating & Cooling
Depending on the size of your Electric heat you can use one set of wires because your unit does not run with the heat like the heat pump. The large set of wires going to the electric heat should be used. You may have to jumper a new set to the contactor. On Goodman unit come in L1 and L2 jumper to contactor. Very simple good luck. Rus
Posted on Jun 21, 2009
Cycle your breakers (turn fff and then on) Check that you are set to cool and not in the middle. You may have a service switch where you change the filter. That has to be on and finally check to make sure that the filter door is securly closed ( some units have a safty switch).
Posted on Aug 18, 2009
Tips for a great answer:
May 21, 2014 | Goodman 3 Ton 14 ee Goodan Heat Pump...
Dec 27, 2010 | Goodman Heating & Cooling
Jul 10, 2010 | Goodman CLQ36AR49 Air Conditioner
Jan 11, 2010 | Goodman PHKJ048-1 Air Conditioner
Jun 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 16, 2009 | Goodman CKL60AR60 Air Conditioner
Jun 10, 2009 | Goodman CKL30AR30 Air Conditioner
Mar 16, 2009 | Heating & Cooling
Jul 06, 2008 | Goodman CLQ36AR49 Air Conditioner
102 people viewed this question
Usually answered in minutes!