Question about Goodman Heating & Cooling
You might have a bad valve on compressor.Close valve on high side and see if the low side pumps down. Of course you should have your gages hooked up.If your low side doesn't pump down you have a bad valve.
Posted on Jul 11, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 10, 2015 | Goodman Manufacturing Goodman...
May 03, 2014 | Goodman Manufacturing Goodman GSZ130301...
May 01, 2014 | Goodman Heating & Cooling
Oct 25, 2013 | Goodman Manufacturing...
Jul 13, 2010 | Goodman CLQ36AR49 Air Conditioner
Jun 07, 2010 | Goodman CLQ36AR49 Air Conditioner
Sep 22, 2009 | Heating & Cooling
Jun 13, 2009 | Ruud UAKA042 Air Conditioner
108 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: