Question about Samsung Heating & Cooling
1. May be your blower motor mechanism locked. Replace bearings or motor. 2. Indoor Pipe Sensor or Outdoor Sensor Assy fault, Open or Short. Disconnect from PCB and measure resistance. Air sensor = 10 kOhm at 25C, Pipe sensor = 5
kOhm at 25C. If not replace sensor.
Posted on Jan 04, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 22, 2015 | Honda CR-V Cars & Trucks
Dec 16, 2014 | Sharp Heating & Cooling
Jun 29, 2011 | Whirlpool ACQ122XK Air Conditioner
Jul 11, 2009 | Heating & Cooling
Jul 08, 2009 | Heating & Cooling
May 28, 2009 | 1996 Toyota Camry
Feb 11, 2009 | Heating & Cooling
Nov 21, 2008 | Nintendo Wii Console
Oct 14, 2008 | Goodman GMS90703BXA Heater
Jun 27, 2008 | Televison & Video
Aug 12, 2017 | Samsung Heating & Cooling
147 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: