Question about Heating & Cooling
Posted by Anonymous on
2 ways 1 place a volt meter in the ingniter plug and wait for the timing of ignite power.if no power disconnect vacume tube off switch at draft motor and clear the port on the furnace houseing, paper clip works well. if port is clear then draft switch may be bad
Posted on Jan 04, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 21, 2015 | Honeywell Heating & Cooling
Oct 04, 2014 | Heating & Cooling
Aug 06, 2017 | Carrier Heating & Cooling
Jan 30, 2014 | Goodman GMS807034ANA Heater
Jan 10, 2014 | Heating & Cooling
Dec 05, 2010 | Goodman GPG152407041 15 SEER Packaged...
Oct 22, 2010 | Heating & Cooling
Oct 29, 2008 | Heating & Cooling
Oct 25, 2008 | Heating & Cooling
Aug 21, 2017 | Heating & Cooling
86 people viewed this question
Usually answered in minutes!