Question about General Electric Water Heaters
That sounds like the TP valve is leaking.
1) Leaking TP valve can be caused by defective TP valve
How to replace TP valve:
2) TP valve can also be caused by overheated tank.
Turn down thermostat.
Install expansion tank on incoming cold water line.
Electric heater: thermostat or element may be bad and tank needs troubleshooting
Gas heater: thermostat is connected to gas valve and gas valve may need replacement.
3) First step is replace TP valve and see if that solves problem.
4) Add a comment for more free help.
Also take advantage of fixyas phone service.
For a price, fixya expert speaks with you over phone while you work on water heater.
Posted on Jan 04, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 28, 2016 | Water Water Heaters
Mar 26, 2013 | Rheem Water Heaters
Nov 04, 2012 | General Electric Water Heaters
Aug 05, 2012 | Rheem 40 GAL ELEC TALL Water Heater 6YR SC...
Aug 28, 2011 | American Standard 40 G Natural Gas Water...
Jun 04, 2011 | RTO Atwood Water Heater - 6 Gal LP
Jan 17, 2011 | Rheem Water Heaters
Dec 19, 2010 | Rheem Water Heater Pressure Relief Valve
Oct 02, 2010 | Whirlpool Water Heaters
Jul 12, 2009 | Water Heaters
Aug 27, 2015 | General Electric Ge Appliances GEH50DNSRSA...
133 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: