Question about Heating & Cooling
There are two things that can cause that...
The first would be a bad board or relay on the board... the relay is not releasing completely or the board is shorting and causing the relay to bump....
The second would be the high limit bumping and triggering the board to bump the motor...
What I would do is to pull one of the wires from the high limit switch right after it runs and shuts down to see if the problem continues... if it does then the board is bad... if it stops and stays off then the high limit is bad... replace that....
Hope you followed all of this and that it helps you...
Posted on Jan 05, 2011
It sounds to me like your fan off limit switch is set to low if its adjustable or almost worn out if it's not adjustable. I would like to be of more help but I need more information,such as age and size of your furnace and type of limit switch if you know. Thank you.
Posted on Jan 04, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2015 | Dayton Gas Furnace Heater
Oct 11, 2014 | Heating & Cooling
Dec 23, 2012 | Carrier Weathermaker 8000 Gas Furnace 125k...
Nov 25, 2012 | Carrier 38CKC042 Air Conditioner
Jan 18, 2010 | Coleman Heating & Cooling
Mar 17, 2009 | Goodman GMS90703BXA Heater
Mar 10, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 26, 2009 | Goodman GMS90703BXA Heater
Oct 30, 2008 | Carrier 38BRC048 Air Conditioner
Jul 06, 2008 | Carrier Heating & Cooling
23 people viewed this question
Usually answered in minutes!