Question about Honeywell Heating & Cooling
Posted by Anonymous on
Make a jumper wire and jump the two terminals where the thermostat wires into the furnace, generally R and W terminals or TT terminals. If unit fires, you have a thermostat or thermostat wire issue. If it still does not run, check for 24 volts at the gas valve. Could have a bad transformer, bad gas valve or the relay for gas valve is bad.
Posted on Jan 02, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 19, 2014 | Pool & Spa
May 28, 2013 | Raypak Pool & Spa
Mar 21, 2011 | Heating & Cooling
Mar 15, 2011 | RELIANCE ELECTRIC WATER HEATER
Apr 12, 2010 | Water Heaters
Feb 06, 2010 | Vulcan GR45 Deep Fryer
May 02, 2009 | Pentair Minimax CH Heater
Jan 26, 2009 | Williams 2509612 Ceramic Mid-Size Heater
150 people viewed this question
Usually answered in minutes!