Question about Sunbeam Heating & Cooling
Have you replaced the thermocouple? Have you cleaned the Pilot? Do you have a strong pilot flame and is it touching the thermocouple? Sometimes if you don't have a good strong pilot is that when you turn the main gas on it pulls the pilot flame away from the thermocouple and cools it off so it drops the signal. Check the gas pressure should have 10 to 11 "WC of manifold pressure.
And you could have a bad gas valve. Hope this helps.
Posted on Jan 02, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 04, 2016 | Empire Comfort Systems DV215SG Gas Wall...
Dec 27, 2012 | Empire Heating & Cooling
Apr 30, 2011 | Endless Summer 92000 Table Top Patio...
Feb 04, 2011 | Empire GWT-50 Wall Mounted Panel Heater
Jan 04, 2011 | Heating & Cooling
Dec 02, 2010 | Heating & Cooling
Dec 08, 2007 | Empire DV-215 Direct Vent Natural Gas...
110 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: