Question about Carrier 38CKC042 Air Conditioner
Carrier fan coil model FB4ANM060 and Carrier condenser model 38ED-060-321. Fan in attic unit randomly turns off and then back on again during first 15 minutes of each cycle, while the outside compressor unit continues running normally, even if the fan remains off for a while.
My e-mail is firstname.lastname@example.org
P.S. Please ignore the incorrect model number I was forced to choose below in order to get this message to send properly.
Turn the power to the indoor unit off. Remove the cover where the fan is. Feel the motor of the fan. If it is very hot the bearings have likely gone out. If the fan is cool to the touch I would call a service company because you likely have an electrical problem that will require some training to solve.
Posted on Feb 20, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
If it is just the condenser fan that means you have a fan relay that has welded shut. Turn power off to your unit and trace the wires from your condenser fan back into the control panel at the unit. You'll have 3 wires going to it. 2 go to the run capacitor and one goes to the fan relay. The one that goes to the fan relay is the part that needs to be replaced. If you have no fan relay and it goes to the main contractor, half of your main contractor is welded shut and will need to be replaced.
Sep 18, 2014 | Carrier 52PQ-515---3 Premier Series Heat...
Jun 25, 2014 | Ruud Central System Air Conditioner
Sep 18, 2012 | Carrier 38CKC036 Air Conditioner
Jul 19, 2012 | Carrier Heating & Cooling
Dec 15, 2010 | Carrier 36KCARMS Air Conditioner
Oct 11, 2010 | Carrier 38CKC036 Air Conditioner
Jan 21, 2010 | Carrier Heating & Cooling
220 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: