Question about Flotec TC2151 P2 Well Pump Pressure Switch
Your pump should have a 20lb seperation ie. pump turns on at 20lb and off at 40lb or on at 50lb off at 70lb. under the cover of the switch theres two screws with springs under them.dont mess with the small one.the large one if you screw it down (right) will increase the pressure while maintaining the 20lb separation. one thing to keep in mind its fine to adjust the pressure BUT at the same time the air pressure in the tank needs to be adjusted to two lbs below the cut in pressure of the pump.
I believe the directions are in the top of the cover of the switch
Posted on Jan 18, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 23, 2014 | Pentair Flotec Fp7110t-08 Water Tank...
Oct 02, 2014 | Plumbing
Nov 12, 2012 | Flotec Corrosion Resistant Shallow Well...
Jan 03, 2011 | Flotec Corrosion Resistant Shallow Well...
Dec 04, 2010 | Electrical Supplies
Nov 14, 2010 | Flotec Plumbing
Nov 09, 2010 | Flotec Electrical Supplies
Oct 30, 2009 | Electrical Supplies
Apr 11, 2009 | Flotec Simer//Omni 2957 Submersible Sump...
May 22, 2014 | Flotec TC2151 P2 Well Pump Pressure Switch
544 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: