Question about Goodman GMS90703BXA Heater
First of all the water is normal in a 90+ efficient furnace. However it should be draining off before there is a problem. If the furnace was installed correctly there will be a couple of drain hoses near inducer motor that lead to a main collector on the side of the furnace. Check that those drain hoses are clear of debris and that the plastic collector on the side of the furnace has standing water in it too. From here continue checking for blockages in the drain system all the way to the floor drain or termination point. Hope this helps.
Posted on Jan 02, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 10, 2013 | Goodman Manufacturing Goodman...
Jan 24, 2008 | Goodman GMS90703BXA Heater
Sep 18, 2012 | Goodman GMS90703BXA Heater
Oct 12, 2011 | Goodman GMS90703BXA Heater
Oct 02, 2011 | Goodman Heating & Cooling
Feb 04, 2011 | Goodman GMS80903BNA Heater
Dec 09, 2010 | Goodman B1859005 Induced Draft Blower...
Oct 17, 2009 | Goodman GMS90703BXA Heater
Nov 18, 2008 | Goodman GMS90703BXA Heater
Oct 28, 2007 | Goodman GMS90703BXA Heater
204 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: