Question about Goodman GMS90703BXA Heater
The first thing to do is verify that you have power to your heater.If you have a volt meter you can remove cover from electric box inside furnace and set meter to a.c. volts and check across black and white wires. You can also turn your thermostat to fan on setting and fan should run if not you may not have power to heater or bad t-stat.
After you're sure you have power to heater turn thermostat to auto and heat. Turn temp setting up high enough to call for heat. See if your induced draft motor comes on. If it does not then check electrical connections or replace draft motor.If you have power to heater and t-stat is good if draft motor does not run then nothing else will work.
You can by pass t-stat to see if it's the problem by removing cover and and taking base off the wall to get to stat wires. Locate wires that are hooked to terminals marked R or Rh and W. Remove these wires and touch them together. If t-stat is bad this should make heater come on and run. If this works then you need to replace stat.
If this does not help you please let me know and tell me what you have found and I will do my best to assist you. Thank you
Posted on Jan 02, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2014 | Heating & Cooling
Nov 05, 2012 | 1990 Toyota Corolla
Sep 03, 2012 | 1993 Buick Park Avenue
May 28, 2012 | Hayward H Series Pool & Spa Heater 400k...
Apr 17, 2012 | Jandy LXI 400 NATURAL GAS POOL HEATER -
Jul 19, 2011 | Whirlpool Water Heaters
Jan 21, 2010 | Hummer H2 Cars & Trucks
Dec 19, 2009 | 2002 Chevrolet TrailBlazer
111 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: