Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Line is L1 L2 L3 to line voltage. wire nut 4-7 together wirenut 5-7 together and wirenut 6-9 together connect 123 to line for low voltage 123 together 456 together 679 together. This works on all dual voltage 3 phase motors. Some of the newer Daytom motors have a plug that you just turn for changing voltage. Rudty
Posted on Jun 07, 2009
Hi, the new motor takes its own capacitor to run it. This is what the 2- brown wires are for, one will have a white stripe. You will need to but a seperate run capacitor for this motor, a 5 uf, 7.5, or what ever it calls for. they should have told you when you bought the motor. It will have to spade connectors on it where the brown wires connect alone. Use the dual capacitor if that is what you have for the other 220 volt wires.Black and purple will be your 2 hot wires.You can connect either one to the old capacitor on the fan terminal and the other to the load side of the contactor, so when the contactor closes it will energize the motor.Or, take both the black and the purple wires and to the load side ( outlet side ) of the contactor, connect one to one side and the other to the other side. The line side is where your 2 hot wires that connect to the contactor from the incoming wires from the electrical box, you want to be on the other end. I would connect the black to the contactor load side and purple to the old capacitor as long as the old wiring is still on it as it has to be fed by a hot wire from the contactor. Each wire, blk, and purple has to have 120 volts to each one and you can get this a couple of ways. The contactor has several terminals that are not used and if you wire them on the outlet side, they will only be energized when the contactor is closed on a call from the stat, very easy to do. You will have to get a coulple of crimp on connectors to put on the ends of the wires, but the brown ones should already have them for this capacitor. Do not try to put the brown wires on the old run capacitor as you will burn out the new motor! Go get the small run cap for these 2 wires for about $10. I know that you can do this wiring change just remember the blk is hot 120, and purple is hot 120, = 240.volts. If you have removed all of the wires from the old capacitor, then use the contactor to connect to. The compressor wires must stay on the old run cap on the hermetic side and this old cap. must be fed by a hot wire from the contactor to the common terminal, that is marked with a C..If you look at the new motor diagram, it will show you also. Please dont forget to rate me as I know you will be kind, and I will check in on you to see how you are doing. Get this capacitor and it will run. This is a must!! Please keep me posted.
A/C, Heating, & Refrigeration Contractor
Posted on Sep 07, 2010
Testimonial: "Very knowledgeable. Easy to follow directions. Truely knows their field."
Tips for a great answer:
Jan 23, 2016 | Dayton Dryers
Mar 23, 2014 | Dryers
May 21, 2013 | Pool & Spa
Oct 12, 2012 | Dryers
Mar 08, 2011 | Kitchen Ranges
Mar 02, 2011 | Dayton Heating & Cooling
Jan 14, 2011 | Dayton Permanent Split Capacitor Motor Fan
Jun 05, 2010 | Dayton Audio Dayton 6K138 CapacitorStart
Dec 13, 2008 | Dayton Permanent Split Capacitor Motor Fan
42 people viewed this question
Usually answered in minutes!