Question about Bryant Heating & Cooling
First thing is to turn off the switch on the side of the furnace, next remove the old thermostat and the wires from it. On the new thermostat you should have y, c,w,g,r therminals. The yellow wire goes to the Y terminal, the white wire goes to the W terminal, the red wire goes to the R terminal, the green wire goes to the G terminal and the C is comonly not used.
Posted on Jan 01, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 21, 2015 | Bryant Heating & Cooling
Apr 19, 2015 | Heating & Cooling
Feb 28, 2015 | Goodman Manufacturing Goodman GMS81005CN...
Nov 19, 2014 | Heating & Cooling
May 27, 2014 | Bryant Heating & Cooling
Jul 19, 2011 | Bryant 462AJC021BA Air Conditioner
Feb 13, 2011 | Hitachi Heating & Cooling
Jan 25, 2011 | Heating & Cooling
Oct 29, 2010 | Goodman GMS90703BXA Heater
166 people viewed this question
Usually answered in minutes!