Question about LG LS122CE Split System Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It is possible that it's the thermostat. When you turn it into cool mode, does the unit come on at all or is it silent? If nothing is coming on, then it's likely it's the tstat. Did the tech check the refrigerant charge while he was there? He should have checked it with the auxillary heat off and the unit just in heat mode. Make sure that the condenser unit outside is coming on when you are calling for cool, If you turn it on and everything comes on, go outside and put your hand on the large copper pipe coming into the unit. In cool mode, this pipe will be cold to the touch and in heat mode, the pipe will be warm to the touch. There isn't much you can do on your own with the exception of changing the tstat. If you can answer some of the questions I have posed, I can try and give you some more answers. Just remember that a check up doesn't mean its a guarantee that something won't happen the next day, it's just that everything was in working order at the time of the checkup.
Posted on Mar 21, 2009
Hi, I looked up you're unit to see just what I already assumed it was, a split system, ductless,9kb.t.u. Ok, 1st go to the outdoor unit to see if it comes on when you turn your t-stat to heating, and be sure you lower the temp. enough to do this test. There maybe a time delay before it starts up, but not long,1-1/2 min. If it doesn't start up, we know that there is a problem.If not on, make sure you check for the power source, locate the breaker it may have tripped, or right at the unit there is a elect. box that should contain 2-fuses.They may be hidden from site under a shield you may have to remove. Check all of this only if this unit is not running. Reset breaker, or replace fuses if not running.If that was the problem and it was off, and now its on, you will have to watch it and if it continues to loose power, you have a problem in a componant as the compressor, condenser fan motor, open or shorted run cap, contactor Ect.You could have developed a freon leak, and it could be off on low pressure.If it is running, it still could be low on freon, reversing valve not changing over, many things can cause this Im afraid to say.The main thing to do or to start, would be to make sure that the outdoor unit is on, fan on, and compressor running if you listen at where the wiring and copper lines enter.You may need to call a tech if you check these things i have suggested and you have no luck. Please be safe and let me know, and we can go from there before you call anyone out.
Posted on Nov 17, 2009
Tips for a great answer:
Sep 16, 2015 | LG Heating & Cooling
on Mar 06, 2010 | Heating & Cooling
Sep 01, 2011 | Fedders A6X05F2D Air Conditioner
Aug 05, 2011 | Heating & Cooling
Jan 21, 2011 | 2000 Jeep Grand Cherokee
Jul 12, 2010 | Whirlwind FH-778 Air Conditioner
Jun 18, 2010 | 2000 Mercury Sable
Jun 21, 2007 | DeLonghi Pinguino PACL90 Portable Air...
Mar 15, 2013 | LG LS122CE Split System Air Conditioner
51 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: