Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: air conditioner
I managed to find the people who supplied the unit, it was still under warranty, and they said it was the thermistors (temprature probes, they replaced both of them) It is now working perfectly!
Posted on Sep 24, 2008
the fan motor bearings need lub....the shaft has a tiny access hole to put some oil into. because the fan shaft is slowing down, it is putting more strain on the voltage current, and eventually the internal breaker shuts down the ac........plus your condenser is not getting enough air accross it, compressor heats up, and it too will shut the unit down......older units have to be oiled every year, and eventually it too will fail, and a new blower motor assembly is needed or replace the ac unit.....blower motor units are around $130....now you install it or pay to have it done at around another $150 labor,,,,,try yourself, if it fails then call the tech........let me know ..ray..firstname.lastname@example.org
Posted on Dec 31, 2008
If the a/c fails to continue to blow cold there could be a few problems you can look for. First once you activate the system check to see if the compressor kicks in. You will hear the compressor humming . Once the a/c quits cooling go and see if the compressor is still running. If its not running its probibly gone into thermal overload (compressor overheated). If that is the case then you need to check to see if the coils are icing up if they are icing up then the problem is with 1) air flow restriction filter dirty, coils dirty simple repairs there replace filter, clean evaporator coil with a coil cleaner that can be purchased at a home repair store cleaning the condensor coil the same. 2) system is low on freon in which case the system will need to be recharged. Also, If you have a digital thermostat replace the batteries that may also be of some help. Good Luck on repairs
Posted on Aug 31, 2009
insufficient cooling have several reason,most common factor is low freon charging due to service factor,defective thermostat control,dirty evaporator and condenser fin,try to check the current rating using ammeter clamp tester if the rated current read in tester below the rated current on tag(compressor)
you need to charge freon,if the fin and evaporator is dirty need to ve clean,if the thermostat is not functioning replace thermostat.
also consider the main defective if the aircon is running chck the compressor if it is running by touching the tip of screw driver to the top body of compressor you can feeel vibration,if compressor is not running yo don't have cooling effect only blowing of air.on repairing this this should be done by a certified aircon technician,have a nice day fix my rate,thank you very much.
Posted on May 14, 2010
Tips for a great answer:
Aug 13, 2016 | Haier Heating & Cooling
Jun 22, 2015 | GE Zoneline In Wall Ptac Unit Air...
Jul 19, 2013 | Sharp Cv-p12lx 11500 Btu Portable Air...
Jun 15, 2011 | 2002 Volvo S60
Nov 09, 2010 | Amana PTH123B35AE Air Conditioner
Jul 05, 2010 | Mitsubishi MS-A09WA Split System Air...
May 22, 2010 | LG Heat cool Window Air Conditioner
Apr 18, 2009 | Fujitsu 24R1 Air Conditioner
Apr 01, 2009 | GE APN08AA Portable Air Conditioner
Jan 07, 2009 | 1998 Ford Escort
56 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: