Question about LG Heating & Cooling
Ch-61.Condenser coil over 65°C. Check coil and filters are clean and free from debris, and airflow is OK. Check system pressures for non-condesables
Clean coil & filter. If non condensable gas, remove gas and flush out the system. Vacuum and recharge.
Posted on Jan 01, 2011
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 04, 2016 | LG Heating & Cooling
Sep 01, 2015 | LG Heating & Cooling
Dec 14, 2014 | Fujitsu Heating & Cooling
Jan 23, 2014 | MGE Galaxy 3000 UPS System
Jan 02, 2014 | LG LS-K2430HL Heat Cool Mini Split Air...
Dec 11, 2013 | Heating & Cooling
Dec 15, 2011 | Insignia Televison & Video
Nov 18, 2010 | LG Art Cool LA181CNW Split System Air...
May 14, 2008 | Fujitsu 24C1 Air Conditioner
Jan 02, 2008 | Heating & Cooling
710 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: