Question about Heating & Cooling
F-6 High discharge coil temp. due toover charged /condenser coil blockage/less rpm of fan motor in outdoor/non-condensate gas.
Purge out over charged gas/clean condenser coil/Replace fan capacitor./Releaseall gas and flush out the system,replace filter drier and vacuum & do gascharging.
Posted on Dec 31, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 31, 2016 | Heating & Cooling
Jun 05, 2016 | Heating & Cooling
Feb 05, 2016 | KitchenAid Microwave Ovens
Sep 09, 2014 | Electrolux Heating & Cooling
Jan 15, 2011 | Dacor Preference RSD30 Gas Kitchen Range
May 09, 2010 | Heating & Cooling
568 people viewed this question
Usually answered in minutes!