Question about Teledyne Laars IGNITION TRANSFORMER
First of all check to see if you need a vent stack wind might be blowing it out if ok then check to see if spider web in pilot generator if ok replace pilot generator turn off gas then follow the small silver tube down under replace the pilot generator
Posted on Jan 14, 2016
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Might be the thermostat itself. If your mechanically inclined, then you can jump the wires at the thermostat to see if the thermostat is bad. It will only be 24v, but try to keep from touching the wires themselfs. Use a pair of needle nose pliers with insulated handles. Take off the front cover of the thermostat and you should see the wires. Depending on the wires they have hooked up, normally it is R- Power, W- Heat, Y- A/C, G- Fan. Without touching anything else, take your pliers and put both tips to R and W, hold it there steadily and wait for it to come on, its best to have someone at the furnace to hear it. If it comes on, then the thermostat is bad, if not, I would need more info on the problem. Hope this helps
Posted on Dec 28, 2009
Tips for a great answer:
Jan 10, 2016 | Robertshaw 720-007 universal gas valve for...
Dec 08, 2015 | Williams Heating & Cooling
Feb 19, 2015 | Dayton Gas Furnace Heater
Apr 04, 2014 | Computers & Internet
Dec 03, 2013 | Teledyne Laars IGNITION TRANSFORMER
you for posting your question here on Fixya.com.
the pilot generator or the pilot head itself is the issue. You need a good,
solid blue flame across the generator to get enough power to hold the switch
open when you let go of the knob. If the pilot flame is week or not aimed
across the generator it will not stay lit.
it is but the generator is old and weak, it will go out as well. If you can see
the pilot flame and it is a nice blue color, replace the generator. If it is
not, disassemble the pilot and either clean it out or replace it.
this answer does not fix your problem, please comment with additional details
prior to rating the answer. You may also contact me thru our website at www.arrowpools.net. Positive feedback is appreciated
once your problem is solved!
Aug 06, 2011 | Jandy Lite 2 Natural Gas Pilot Light...
Dec 21, 2010 | Heating & Cooling
Nov 12, 2009 | Heating & Cooling
Mar 04, 2007 | Williams 2509612 Ceramic Mid-Size Heater
162 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: