Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hopefully there are markings on the old t-stat as to what terminal is what.
on the honeywell 8000 use the heat pump labeling and then the standard wiring would be
There should not be a bare wire, it probably just has the insulation stripped back way too far.
You should probably open the furnace and compare the terminal label in the furnace to the wire color. normally yellow and blue pass through the furnace and are wire nutted to wires going to the outdoor unit. In the furnace the white wire will connect to the w or w1 terminal. also, you will need to set the Honeywell stat to have the following parameters.
other parameters that I did not specify, you may read the manual and make your own decision but I recommend factory settings for the other parameters
Posted on Jun 18, 2008
Thanks for the response, to be more specific, the nine pin connector was damaged, but I was able to connect the wires back to main unit panel. I am ready to hook to the hunter thermostat and do not know which wires to connect to. This is my problem and I do not want to short something out. Hope this helps, I want to get it installed again. Thanks again for caring....Jerry
Posted on Aug 16, 2008
Posted on Aug 28, 2008
First, let me say that if you're not entirely comfortable doing high voltage electrical work, you might want to call an electrician. It's not impossible for you to get hurt or killed or burn down your house. At least be sure to turn of the circuit breaker while you're working on it.
The blacks and whites twisted together are passing through power to other parts of your premises and are always on, so be sure to keep them twisted together. The red is the one that will take power from your light switch and send it to your light fixture.
At the fixture, connect the white to white and red to black, the same as before. At the light switch, connect the black to one side of the switch and the red to the other. When you turn on the switch, it will permit power from the black to travel down the red to the fixture, and from the fixture, the circuit will be completed through the white.
Posted on Sep 12, 2009
Tips for a great answer:
Jul 17, 2013 | Coleman 7990-319p Evcon Gas Furnace...
Jul 18, 2017 | Heating & Cooling
Turn the Coleman furnace system switch to the "Off" position on the electric service panel.
Locate the manual reset switch near the left side of your furnace blower. Your Coleman furnace has an upper limit switch for manual reset and a lower limit switch for automatic reset.
Press the reset button, which you will find in the middle of the limit switch. Use this manual reset button when the furnace burner will not operate. (See Reference 1 pg 4 "The Furnace Controls and their Function/Important" & Reference 4 # 3)
Turn the system switch to the "On" position.
Jul 29, 2012 | Coleman Heating & Cooling
Dec 08, 2017 | Coleman Propane Forced Air Heater...
Oct 10, 2010 | Heating & Cooling
Dec 09, 2009 | Coleman Propane Forced Air Heater...
Oct 26, 2009 | Coleman 10' X 10' Sundome Tent 9160K101
Apr 10, 2009 | Honeywell Electronic Programmable...
Jan 19, 2009 | Coleman Propane Forced Air Heater...
Jan 16, 2009 | Coleman Propane Forced Air Heater...
56 people viewed this question
Usually answered in minutes!