Question about Hayward H Series Pool & Spa Heater 400k Btu Propane Gas Milivolt Ignition H400p1
YOur 1f code is actually a IF code which stands for "ignition failure".
This can be caused by many things, but the most likely is either the ignitor has failed, or the flame sensor has failed.
Make sure the gas manual gas valve is open. Remove from panel so that you can see the ignitor.
Turn off power, then turn back on. After 90 seconds, the ignitor should start to glow red hot. If this is not occuring, then it is likely the ignitor or ignitor wiring.
If the ignitor does glow, then the heater ignites, but still goes off showing the IF code, then it is the flame sensor.
If the ignitor glows, and the heater does not ignite, it is likely the gas valve or ignition control.
As stated above, the ignitor is most likely.
Posted on Dec 31, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 20, 2015 | Pool & Spa
Aug 09, 2014 | Hayward Pool & Spa
May 08, 2014 | Hayward 250kbtu Ng Pool Heater - Inground
Dec 30, 2010 | Hayward H400fdp Low Nox Propane Swimming...
May 22, 2010 | Hayward 250FDP Universal Series Propane...
May 05, 2010 | Hayward 250kbtu Ng Pool Heater - Inground
Jun 28, 2009 | Hayward H Series Pool & Spa Heater 400k...
Feb 28, 2009 | LG 24 in. LD-12BS6 Stainless Steel...
647 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: