Question about General Filters 1042-LH Humidifier
I would first check to make sure you have water to incoming side of the solenoid valve. Most inlet and outlet fitting are compression type so you can carefully loosen nut on incoming side to see if you have water there.You don't want to take the nut off just back it off a liitle to see if you have pressure there.If so then retighten nut on incoming side and loosen nut on leaving side. Turn up thermostat to actuate solenoid valve.You should be able to hear a slight click when the valve opens.
If you have water on incoming side and you can tell that valve is working but you are not getting water flow then shut off water supply to humidifier and remove inlet nut and and slip pipe back to see if there is a blockage there. Clean as needed or replace solenoid if it's not working.If you have flow into unit but not out then check outlet side for blockage. I hope this helps . Thank you.
Posted on Dec 30, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 27, 2014 | General Filters Humidifiers
Jan 22, 2012 | Honeywell HE220A1019 Whole House...
Nov 17, 2011 | General Filters 1099-LH Humidifier
Jan 25, 2011 | General Filters 1042-LH Humidifier
Dec 01, 2009 | General Filters 1042-LH Humidifier
Jan 27, 2009 | General Filters 1099-LH Humidifier
Jan 16, 2009 | General Filters 1042-LH Humidifier
Dec 20, 2008 | General Filters 1042-LH Humidifier
181 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: