Question about Goodman CLQ36AR49 Air Conditioner
I have condensation leaking down through unit. This just started this year I replaced the fan motor this winter did I forget to replace something? I can see the condensation accumaliting in the tray but it never gets high enough to run through the pvc pipe. I am concened that the water will end up damaging the furnace parts under the coils.
This may be caused by an un level unit, or the A-coil itself may be un level did you move it when you replaced the fan motor? The second thing to check is the fitting at the condensate drain pan to make sure the weld has not broken or the fitting has not been stressed or bent and have a small crack.
Hope this helps Ya
please rate me
Posted on Jul 19, 2008
Tips for a great answer:
Jun 03, 2014 | Air Conditioners
Sep 02, 2013 | Frigidaire Air Conditioners
Sep 18, 2012 | Carrier 38CKC036 Air Conditioner
Jul 21, 2011 | Air Conditioners
Jul 12, 2011 | Air Conditioners
Dec 23, 2009 | Convair Portable Air Conditioner
Jan 23, 2009 | Air Conditioners
Jul 08, 2008 | Air Conditioners
121 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: