Question about Goodman CLQ36AR49 Air Conditioner
I have condensation leaking down through unit. This just started this year I replaced the fan motor this winter did I forget to replace something? I can see the condensation accumaliting in the tray but it never gets high enough to run through the pvc pipe. I am concened that the water will end up damaging the furnace parts under the coils.
This may be caused by an un level unit, or the A-coil itself may be un level did you move it when you replaced the fan motor? The second thing to check is the fitting at the condensate drain pan to make sure the weld has not broken or the fitting has not been stressed or bent and have a small crack.
Hope this helps Ya
please rate me
Posted on Jul 19, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 03, 2014 | Heating & Cooling
Sep 02, 2013 | Frigidaire Heating & Cooling
Sep 18, 2012 | Carrier 38CKC036 Air Conditioner
Jul 21, 2011 | Heating & Cooling
Jul 12, 2011 | Heating & Cooling
Dec 23, 2009 | Convair Portable Air Conditioner
Jan 23, 2009 | Heating & Cooling
Jul 08, 2008 | Heating & Cooling
121 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: