Question about DeLonghi Heating & Cooling
Locate and touch the cooils located, usually, above the condensate collection pan, ("pail empty"). If the coils are not cold, or cool to the touch, the unit has lost its charge of refrigerant. This would explain why the unit fan is working, but there is no condensate, as there is no coolant (charge) to cool the coils and "pull" the hunidityout of the air.
Posted on Jul 08, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 05, 2014 | Frigidaire Dehumidifier Compressor...
Aug 20, 2013 | Therma-Stor Santa Fe Dehumidifier
Aug 31, 2011 | DeLonghi DE500P Dehumidifier
Jul 28, 2011 | Danby DDR5009EE Dehumidifier
Jun 04, 2011 | Danby DDR451 Dehumidifier
May 26, 2011 | DeLonghi DE500P Dehumidifier
Aug 11, 2010 | DeLonghi DE500P Dehumidifier
Mar 23, 2010 | Haier Dehumidifiers
May 13, 2009 | Frigidaire Dehumidifiers
Feb 16, 2009 | Danby DDR586R Dehumidifier
Mar 08, 2017 | DeLonghi Heating & Cooling
122 people viewed this question
Usually answered in minutes!