Question about LG Heating & Cooling
CH46 Outdoor unit suction sensor fault. Disconnect from PCB and measure resistance. 10 kOhm at 10°C and 4 kOhm at 30°C. If OK replace PCB, if not replace sensor. Helpful?
Posted on Dec 30, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 01, 2015 | LG Heating & Cooling
Oct 12, 2013 | Sharp Heating & Cooling
Jul 30, 2013 | Fujitsu 24C1 Air Conditioner
May 11, 2013 | Sharp Heating & Cooling
May 27, 2012 | Sharp Heating & Cooling
Apr 30, 2009 | LG Art Cool LA181CNW Split System Air...
Mar 09, 2009 | Sony KDF46E2000 46" Projection HDTV
Nov 18, 2008 | Office Equipment & Supplies
726 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: