Question about Dometic Rooftop RV Air Conditioner
Repair line leak vac and gas up 68 psi. unit was cooling good. left running for about 45 min and unit was not cooling pressure was 75 to 120 psi
Exactly how much refrigerant did you charge into the system when you recharged it? If the suction pressure is varying that much you most likely over charged the system and got a liquid flood back which took out the compressor valves.
Posted on Jul 07, 2008
Tips for a great answer:
Apr 24, 2015 | Air Conditioners
May 23, 2014 | Hitachi RAS-09UH Air Conditioner
Jul 21, 2013 | LG LAN240HSV2-LAU240HSV2 24000 BTU 20 SEER...
Apr 25, 2011 | Air Conditioners
May 17, 2010 | Goodman CLJ24AR32 Air Conditioner
Mar 31, 2010 | Air Conditioners
Sep 28, 2009 | Intertherm P3RA-048K Air Conditioner
Jul 14, 2009 | LG LS092CE Split System Air Conditioner
Apr 22, 2008 | LG LSC091PMA Split System Air Conditioner
97 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: