Question about Heating & Cooling
You may have a couple of problems now. The original issue of icing up is most commonly due to low refrigerant in the a/c. For this you will need a professional to correct.
The second problem sounds like it may be a bad capacitor for the indoor blower motor. This is a common occurrence after a system freezes. Often the water that leaks from the A/C will get slung around by the fan causing the water to cause a short on the capacitor. The capacitor is a silver/gray electrical component that usually stands alone from the rest of the circuitry. It is cylinder shaped and has two wires (usually brown) connected to one end of it. It is common practice in the business to replace both the motor and the capacitor after this kind of water damage.
Posted on Jul 07, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 16, 2015 | Chevrolet Cars & Trucks
Jun 17, 2017 | Coleman Heating & Cooling
Dec 28, 2010 | Heating & Cooling
Jul 08, 2010 | Dometic Rooftop RV Air Conditioner
Oct 09, 2009 | 2003 Ford Focus
Jul 06, 2009 | Dometic Rooftop RV Air Conditioner
Jun 25, 2009 | Dometic Rooftop RV Air Conditioner
Jun 20, 2009 | Whirlwind FH-778 Air Conditioner
Mar 29, 2009 | Kenmore Refrigerators
Oct 31, 2008 | Sharp CV-P09FX Air Conditioner
98 people viewed this question
Usually answered in minutes!