Question about Bryant Heating & Cooling
Posted by Anonymous on
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Is this a package unit??? Or is it inside the home?? How old is the furnace. The first thing to do is axcess the fan and see if it is controlled by a computer or its old enough to have a fan switch. Trace the red wire from the fan mtr that should take you to the fan switch
Posted on Dec 01, 2007
Are you a qualified refridgerator mechanic with an eletrical liscence? If not get someone who is because doing it yourself will not only void the warranty of the unit but will also void your house and contense insurance in the event of a fire.
Posted on Mar 16, 2008
Make sure the unit is properly set up (jetted/orifices) for LP. It sounds to me like the unit is setup for natural gas and is being used on propane.
Posted on Mar 01, 2009
try checking the pressure sensing switch,it has a tube that should run somewhere close to the inducer fan.sometimes this hose fills with liquids,and makes the units act funny.I don't know if you have a condensing unit or what.the furnace wont try to light if it cant tell the inducer motor is running.any induced draft unit will work this way.you can also do a temp. bypass of the pressure switch to make sure the contacts on it are closing just be sure your inducer fan is running,and you cant leave it like that its just a test.that is a safety feature you really need.
Posted on Mar 19, 2009
if your power vent moter is not running you should not have have glowing ignitor.Frist the vent moter must close an air prove switch in series with the idnitor .seems you have a stuck air prove switch.Its the one with a hose attached
Posted on Apr 07, 2009
Tips for a great answer:
Jun 20, 2011 | American Standard WCZ036F Air Conditioner
Mar 02, 2011 | Heating & Cooling
Dec 20, 2010 | Heating & Cooling
Nov 29, 2010 | Heating & Cooling
Nov 08, 2009 | American Standard 40 G Natural Gas Water...
Oct 05, 2009 | Microsoft Xbox 360 Controller
Jul 08, 2009 | Dometic Rooftop RV Air Conditioner
Jun 02, 2009 | Carrier Heating & Cooling
May 07, 2009 | Heating & Cooling
Aug 21, 2007 | Dometic Rooftop RV Air Conditioner
63 people viewed this question
Usually answered in minutes!