Question about Pentair Heater Thermistor Probe 471566
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
1. There is air in the gas line. Power down the heater and allow it to try igniting until lockout. If it locks out, repeat the process. Most lines will clear within 4-5 attempts to ignite.
2. A plugged burner orifice. Run a small pipe cleaner in the brass fittings on the burner tray. They may have small webs in them restricting gas flow.
If the unit is a Standard (STD on the plate inside) it has a flame sensor that may also be bad. That sensor is on the end of the single wire that is cloase to the ignitor wire near the burners. Also check for a losse ground wire on the heater.
Posted on Dec 21, 2008
Sounds like the controller is the problem. This is the circuit board that has the display and controls on it. You can swing that panel open and try tapping on the white plastic cover the controller is under that. This might get the fan relay to release but you will have to replace the controller it will stick again
Posted on Jun 23, 2009
Tips for a great answer:
Jun 05, 2016 | Pentair Minimax NT Heater
Jun 04, 2014 | Pentair Minimax NT Heater
Aug 31, 2011 | Pentair Minimax NT Heater
Aug 14, 2011 | Pentair Minimax NT Heater
Oct 10, 2010 | Pentair Minimax NT Heater
Jul 30, 2010 | Pentair Minimax NT Heater
Jul 09, 2009 | Pentair Minimax NT Heater
Jun 06, 2009 | Pentair Minimax NT Heater
Jun 15, 2017 | Pentair Pool & Spa
321 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: