Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
if it is a Heat pump style the rev valve is in the Freon lines you will have to pull the unit out into the room out of it's sleeve which will stay in the wall ....it rev the flow of refrigerant is it cooling ok?? there is a solenoid on that valve that may be bad i would check that first you will have to look to see if it is energized in the heat or cool mode first to make sure it is switching it should look like a sideways tube with 3 outlets on one side and 1 inlet on the top and the solenoid coil as well with 2 wires going to it let me know what you find out ...1 Note the unit may have electric heat and the element maybe out you will have to pull to check
Posted on Jan 24, 2008
Hopefully there are markings on the old t-stat as to what terminal is what.
on the honeywell 8000 use the heat pump labeling and then the standard wiring would be
There should not be a bare wire, it probably just has the insulation stripped back way too far.
You should probably open the furnace and compare the terminal label in the furnace to the wire color. normally yellow and blue pass through the furnace and are wire nutted to wires going to the outdoor unit. In the furnace the white wire will connect to the w or w1 terminal. also, you will need to set the Honeywell stat to have the following parameters.
other parameters that I did not specify, you may read the manual and make your own decision but I recommend factory settings for the other parameters
Posted on Jun 18, 2008
The digital thermostat must be programmed for GAS heat.
If the problem occured before the t-stat change and is still happening, the problem would be with ignition within the furnace.
Posted on Mar 15, 2009
if your power vent moter is not running you should not have have glowing ignitor.Frist the vent moter must close an air prove switch in series with the idnitor .seems you have a stuck air prove switch.Its the one with a hose attached
Posted on Apr 07, 2009
If you look at control box at roof unit, they usually use a separate set of wires for furnace. See what colors they are attached to at harness to thermostat. Some just follow other harness, and come out at thermostat. (bypass control box) Once you've determined which 2 they are, join them together & see if furnace starts, as it should. If it does, thermostat is faulty. If not, pull outside cover off & check voltages at furnace. I'm guessing by furnace model that your unit is approx 30 ft , but if it's a park model, you may have 24 volt system on furnace or 12 volt. Another way of confirming is to go to back of furnace where air intake grille is inside your unit, and locate 2 blue wires going to furnace & remove whatever wires are attached to them & connect them together. Furnace should start up.
Posted on Jul 08, 2009
Testimonial: "thanks for the link. info solved my problem."
Tips for a great answer:
Oct 31, 2017 | Heating & Cooling
Jan 11, 2014 | Rheem Heating & Cooling
Mar 11, 2011 | Honeywell CT87B ROUND HEATING&COOLING...
Jan 20, 2011 | Honeywell Electronic Programmable...
Mar 21, 2010 | Honeywell Programmable Thermostat Heater
Feb 26, 2010 | Honeywell Programmable Thermostat Heater
Nov 01, 2009 | Heating & Cooling
Dec 18, 2008 | Ruud UBHC Air Conditioner
32 people viewed this question
Usually answered in minutes!