Question about Dayton Gas Furnace Heater
On the side of the heat exchanger is a fan Klixon that turns that motor on when the temp exceed 110f on the side of the heater. maybe that thang is going out or your fan motor needs oiling and is cutting out on overload. Next to the fan klixon is usually a limit. Both look the same. The fan klixon will have a marking stamped into the metal such as F-120 the limit will have L-240.
Posted on Dec 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 26, 2013 | Ingram's Water and Air 100,000 BTU RHEEM...
Oct 17, 2013 | Dryers
Dec 16, 2012 | Heating & Cooling
Nov 24, 2012 | Dayton Gas Furnace Heater
Jan 07, 2011 | Dayton Gas Furnace Heater
Dec 28, 2010 | Heating & Cooling
Nov 13, 2010 | Dayton Gas Furnace Heater
Jan 10, 2010 | Dayton Gas Furnace Heater
Jun 03, 2017 | Heating & Cooling
Nov 01, 2008 | Dayton Gas Furnace Heater
455 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: