Question about Whirlpool Dryers
An electric dryer must be on a circuit by itself. If you lost power to downstairs sockets, you will need an electrician to separate the 120volt side from the 240volt side. You may not have a problem at all with the dryer. If another appliance was operating at the same time as your dryer, that appliance would have overloaded your circuit and tripped the breaker. Please have this looked into by an electrician to avert a possible fire!
Your tech should have recognized this situation or maybe I have misunderstood the issue, but I gave my opinion based on the question above,
If my assistance helped resolve this issue, please show your appreciation by rating how effective my advice was in resolving this issue.
Dave E. (Illeagle)
"Your satisfaction is my personal reward"
Posted on Jul 07, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 17, 2011 | Kenmore 73952 Gas Dryer
Apr 14, 2008 | GE Profile Harmony DPGT750EC Electric...
The circuit breaker may be tripping because of a fault with the dryer or it may be a fault with the circuit breaker being weak.
From the description you give the circuit breakers trip frequently.
I'd suggest you first try selecting the no heat air fluff cycle and run it to see if the breaker trips. If the circuit breaker doesn't trip in air fluff then there is likely a short in the heating element.
With a clamp-on amp meter you can read the amp draw of the dryer when it is heating. With the motor and element both working you would see approximately 25-26 amperes being drawn. The breaker is rated at 30 amps. If the breaker trips and only 26 amps are being drawn then the breaker is the problem.
Try the air fluff cycle first and see if the breaker will trip. Then with additional details I may be able to help you further.
Jan 05, 2011 | Kenmore Dryers
Dec 24, 2010 | Dryers
Oct 01, 2010 | Frigidaire Electric Dryer
Jun 09, 2010 | GE DBSR453EBWW Electric Dryer
Jan 19, 2010 | Abbaka White Knight 44AW Electric Dryer
Sep 21, 2009 | Whirlpool Duet Sport 6.7 Cu. Ft. Gas Dryer
Aug 11, 2009 | Kenmore 800 7982 Dryer
Mar 24, 2007 | Whirlpool LER2614JQ Electric Dryer
Jan 17, 2017 | Whirlpool Dryers
41 people viewed this question
Usually answered in minutes!