Question about Coleman Heating & Cooling
If the thermostat is ok which it probably is then your sequencer is most likely stuck i would say. You could verify that by removing 24 volts to the sequencer to see if it will shut down the heater
When low voltage from the thermostat is applied at the base of this sequencer it heats a bi-metal and turns on each coil and fan in a sequence that will insure the breaker don't throw from the power surge AND warm air comes out the vents when that fan comes on. I would start there.
Posted on Dec 28, 2010
I have an Electric Furnace that blew the transformer and the reverse thermostat relay, Have replace them both and the Heat and fan sequence the side the marked M1, M2, M3 M4 showed signs of overheating that also has been replaced, but overall since the transformer and the other componets have been replaced the heating coils have not kicked and when the heating switch on the furnace it push the blower just wants to run continous
Posted on Jan 14, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2016 | Coleman Heating & Cooling
Jul 12, 2015 | Coleman Heating & Cooling
Sep 29, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Nov 28, 2013 | Heating & Cooling
Jul 17, 2013 | Coleman 7990-319p Evcon Gas Furnace...
Dec 01, 2012 | Coleman Evcon Furnace Control Circuit...
Oct 26, 2009 | Coleman 10' X 10' Sundome Tent 9160K101
Mar 31, 2009 | Coleman Propane Forced Air Heater...
May 30, 2008 | Heating & Cooling
352 people viewed this question
Usually answered in minutes!