Question about Carrier 38CKC036 Air Conditioner
With this cold weather, -- it is not likely tripping off because it is too hot!
Are you familiar with the history of this unit?-- Like has it tripped in the past during HOT weather?
This might be a clue, that the circuit is really loaded close to its limit--
This leads to the next possibility: That the breaker is getting weak (They do after many hard starting loads!
Now-- If you can get the system to start and run for just a few seconds-- can you put a Clamp around Amp meter on the wires?-- and read the full load current?
How close is this to the rating of the circuit breaker?
Is the breaker, and the wire size marginal?
Another thing to look for, is loose lug screws at the main fuses, and the Main contactors, and the motor leads--- for loose wires result in overheating, which raises the current, and leads to tripping, too.
How long ago was the condenser cleaned-- this leads to high amp draw too.
But the first thing would be to learn more about the age of the Main Breaker, and what the 'normal' run current is for that system.
Posted on Dec 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 27, 2016 | Traulsen Refrigerators
Oct 06, 2012 | Bryant /murray Bj2200 Main Circuit Breaker...
Mar 29, 2011 | Mastercool 67471 Evaporative Cooler Air...
Jan 21, 2011 | Heating & Cooling
Jul 14, 2009 | Siemens /ITE 100Amp 2-pole molded circuit...
Jun 09, 2009 | Weather King 10AJA6001AH Air Conditioner
Jun 04, 2009 | Dometic Rooftop RV Air Conditioner
Aug 10, 2008 | Intertherm Heating & Cooling
Mar 09, 2008 | Ovens
Feb 02, 2008 | Whirlpool LER5636P Electric Dryer
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
108 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: