Question about Honeywell 360B Humidifier
Is the saddle valve open? if it is check for sediment build up in it, if it;s clear you will need a new saddle valve. If the fan is not running than most likely you are not getting power to the humidifier, check for 24 volts to the solenoid valve. By the way do you have a current sensing relay or sail switch hooked up to this humidifier?
Posted on Dec 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 30, 2013 | Aprilaire 700 Humidifier
Feb 03, 2011 | Honeywell HE365 Humidifier
Jan 25, 2011 | General Filters 1042-LH Humidifier
Nov 26, 2010 | Honeywell HE365 Humidifier
Nov 13, 2010 | Aprilaire 700 Humidifier
Mar 19, 2010 | Humidifiers
Dec 13, 2009 | Honeywell HE220A1019 Whole House...
Nov 28, 2009 | Honeywell HE260A1010 Whole House...
Nov 22, 2008 | Honeywell HE365 Humidifier
135 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: